Method and maintenance of starting battery for diesel generator setAs for the method and maintenance of starting battery of diesel generator set, the experts give the following Suggestions:
To be safe, wear an acid-proof apron and a mask or protective mirror when maintaining the battery. If the electrolyte accidentally splashes on the skin or clothes, rinse immediately with plenty of water.
The battery is dry when it is first delivered to the user at random, so the electrolyte of the correct proportion (1:1.28) that has been uniformly mixed should be added before use. Unscrew the top cover of the cell and slowly inject the electrolyte between the two dials at the top of the sheet metal and as close as possible to the upper one. After the addition, please do not use immediately, you should first leave the battery for about 15 minutes.
When charging the battery for the first time, it should be noted that the continuous charging time should not exceed 4 hours. Too long charging time will damage the service life of the battery.
When one of the following situations occurs, the charging time is allowed to be extended appropriately:
(1) the battery can be stored for more than 3 months, and the charging time can be 8 hours
(2) that persists for more than 30 ℃ environment temperature (86 ° F) or relative humidity higher than 80% continuously, charging time is 8 hours
(3) if the battery has been stored for more than 1 year, the charging time can be 12 hours
(5) at the end of charging, check whether the liquid level of electrolyte is sufficient, and if necessary, add standard electrolyte with correct specific gravity (1:1.28).
Room 360 green data center remind: to recharge the battery, should first open the battery filter cap or vent cover, and check the electrolyte level, with distilled water to adjust when necessary. In addition, the long-term closed to prevent pollution gas in the battery case is not discharge in time and avoid water at the top of the inside of the cell walls of condensation, it should be paid attention to special vent open, to ease the flow of air is appropriate.
Note: we are not equipped with electrolyte due to corrosion of diesel generators caused by electrolyte spilling out during transportation. (electrolyte is also a standard and common product that users can easily buy.)